Enphase; Canadian Solar 11000W Grid-Tied System
- EECS-11000 Grid-Tied Kit
- This fast and easy 250 watt solar panel system employs microinverter technology to simplify design and installation. We're always looking for ways to make solar easier and more cost effective for homeowners. Independent minded customers are the inspiration behind our solar kits which provide quick and easy installation. Our system includes a grid tied microinverter per panel, Enphase cable drops portrait or landscape with clips and end caps. Choose the system that best fits your available space and budget with the knowledge you can expand your kit at any time down the road.
- Only: Buy Now
- Product Details:
Enphase, Canadian Solar 11000W (11 kW) Grid-tied Microinverter Package
|Kit Description||Part Number||STC* Array Size||Monthly kWh @ 5 Sun Hours /Day STC*||Enphase Inverter Model||Type||Panel & Inverter Warranty|
|11,000 Watt, 44 Panel Enphase Microinverter Kit||EECS-11000||11,000 Watts||1,650 kWh||ENPHASE, M215-60-2LL-S22-IG||Grid Tied Microinverter||25 Years|
CS6P-250P is a robust solar module with 60 solar cells. These modules can be used for on-grid solar applications and are a good fit with Enphase microinverters. Canadian Solar's meticulous design and production techniques ensure a high-yield, long-term performance for every module produced. Canadian Solar's rigorous quality control and in-house testing facilities guarantee Canadian Solar's modules meet the highest quality standards possible.
Best Warranty Insurance - 25 years worldwide coverage 100% warranty term coverage providing third party bankruptcy rights. Non-cancellable insured by 3 world top insurance companies
Enphase Energy inverter is attached to the back of each 250W solar panel which allows each panel to operate independent of each other. Enphase was one of the original inverter manufactures to create a panel level inverter that is fast, easy, safe to install and essentially plug-n-play. The microinverter is attached to the back of each solar panel which allows each panel to operate independent of each other. Each microinverter provides individual maximum power point tracking at the panel level. This advantage significantly reduces planning and performance obstacles such as shading issues or panels on different planes. If no such conditions exists, then the advantage over a central inverter does not exist. Each of the microinverters that makes up the kit integrates with optional Emphases network technology allowing you to monitor each panels performance throughout the day which is a very cool feature if you are a techie. Install an NEMA3 combiner box at a suitable location on the solar racking system. You can center feed the branch, or you can install the combiner box at the end of a row of solar panels. Provide an AC connection from the AC combiner box back to the electrical utility connection using equipment and practices as required by the NEC and your local jurisdiction.
Each of the microinverters that makes up the 11000W solar kit integrates with Enphase network technology allowing you to monitor each panel performance throughout the day. (Monitor is Optional) Enphase system monitoring capability be accomplished using the optional Envoy monitor by simply plugging into a 120 volt wall outlet. You can also track your solar production by using other different types of monitors, but most customers would opt for the Envoy monitor because you can read individual panel performance rather that the whole systems performance.
Because you do not use a DC combiner with breakers, the cost of the microinverter VS a central inverter is offset somewhat. Finally a home solar package that matches the 25 year guarantee on the solar panels with a 25 year guarantee on the inverter. Blue Pacific Solar has done all the work for you with this efficient simple grid-tied home solar system. Following our line drawings you will end up with an NEC (National Electric Code) compliant home solar system with a life expectancy of well over 25 years.
What's On the Truck:
- 44 -Canadian Solar, CS6P-250P 250 Watt Panels, Black Frame, (Equal or Better Subject to Inventory)
- 44 - Enphase M215 Microinverters M215-60-2LL-S22-IG-IG
- Required Number Enphase 240V Single Phase Cable Drops, End Caps and Connectors for Kit.
- 1 Line Drawing; Full Instructive Three-Line Diagram of Entire DC Circuit, as Well as AC Lines to Your Metered Service Entrance.
Product Ships in 3 - 5 Business Days After Funds Clear
*STC - To learn more about solar panels and how they are measured you need to know what STC stands for. STC in an acronym for "Standard Test Conditions". All solar panels are rated in Watts. The watt rating is how much power (amps times volts) the panel will produce in full sunlight at 25 degrees C (77F). This is the industry standard (STC) for all PV panel ratings (PV means Photovoltaics which is a fancy word for solar). Solar panel manufactures have long used this test standard which is 1,000 watts per square meter solar irradiance, 1.5 Air Mass and a 25 degrees C. cell temperature.
PTC is an acronym for "PV-USA". The PV-USA test conditions was developed at the PV USA test site at the University of Davis, California for standards established by the California Energy Commission that are considered closer to real world conditions (Real World Vs STC factory test conditions). The PTC rating test is 1,000 watts per square meter solar irradiance, 1.5 Air Mass, and 20 degrees C. ambient temperature at 10 meters above ground level and wind speed of 1 meter per second. In California, solar panels manufactures must be tested and rated independently at the PV USA test facility at the University of Davis (CA) to be considered for rebates.
The ambient temperature rating (PTC) is generally considered a better real world standard than factory conditions because silicon solar cells average about 20 degrees C. above ambient temperature in the real world, cell voltage drops as temperature increases. A module's power output in real life conditions is lower than the power measured at the panel manufacturing factory where cell temperature is maintained at a controlled 77 degrees F. (25 C).
STC Vs PTC Cell voltage drops about 0.08 volts per degree C. in environments which exceed 25 degrees C. That means an STC rating of 17 volts can actually become a PTC (PV-USA) rating of 15 or 16 volts. Using Ohm's Law, volts times amps is equal to watts which equals power, so a reduced voltage, means reduced watts.
Neither PTC nor STC account for all "real-world" losses. Actual solar systems will produce lower outputs due to soiling, shading, module mismatch, wire losses, inverter and transformer losses, shortfalls in actual nameplate ratings, panel degradation over time, and high-temperature losses for arrays mounted close to or integrated within a roofline.
Enphase M215 Micro Inverter
|Recommended input power (STC)||190 - 260W|
|Maximum input DC voltage||45V|
|Peak power tracking voltage||22V - 36V|
|Min./Max. start voltage||22V / 45V|
|Max. DC short circuit current||15 Amps|
|Max. input current||10.5 Amps|
|Maximum output power||215W|
|Nominal output current||0.9A (arms at nominal duration)|
|Nominal voltage/range||240V / 211-264V|
|Extended voltage / range||240V / 206-269V|
|Nominal frequency / range||60.0 / 59.3-60.5 Hz|
|Extended voltage / range||240V / 206-269V|
|Nominal frequency / range||60.0/59.3-60.5 Hz|
|Extended frequency range||960.0/59.2-60.6 Hz|
|Maximum units per 20A branch circuit||17 (single phase)|
|Maximum output fault current||1.05 Arms, over 3 cycles; 25.2 Apeak, 1.74ms duration|
Enphase microinverter Efficiency
|Inverter CEC weighted efficiency||96.0%|
|Peak inverter efficiency||96.3%|
|Static MPPT efficiency (weighted, reference EN50530)||99.6%|
|Dynamic MPPT efficiency||99.3%|
|Night time power consumption||Night time power consumption|
|Ambient temperature range||-40ºC to + 65ºC|
|Operating temperature range (internal)||-40ºC to + 85ºC|
|Dimensions (W x H x D)||17.3 cm x 16.4 cm x 2.5 cm (6.8” x 6.45” x 1.0”)*|
|Weight||1.6 kg (3.5 lbs)|
|Cooling||Natural convection - No fans|
|Enclosure environmental rating||Outdoor - NEMA 6|
|Compatibility||Pairs with most 60-cell PV modules|
|Warranty||25-year limited warranty|
|Monitoring||Free lifetime monitoring via Enlighten software|
|Compliance||UL1741/IEEE1547, FCC Part 15 Class B CAN/CSA-C22.2 NO. 0-M91, 0.4-04, and 107.1-01|
|*Canadian Solar, CS6P-250P 250W PV Module, H4, PV Wire, 12AWG, 40mm Black Frame, 60 Cell Poly, 25 Year Warranty.|
|Open Circuit Voltage (VOC)||37.2 Volts|
|Maximum Operating Voltage (Vmpp)||30.1 Volts|
|Short Circuit Current (Isc)||8.87 Amps|
|Maximum Power Current-IMP (A)||8.3 Amps|
|Maximum Power at STC (Pmax)||250 Wp|
|Maximum System Voltage (NEC)||600 VDC|
|Short-circuit current temperature coefficient||+0.043%/P|
|Open-circuit voltage temperature coefficient||45/C|
|Peak power temperature coefficient||-0.43%/C|
|Power measure tolerance||+/- 5%|
|Surface burden maximum load capacity||ISO 9001 quality standards and ISO 14001 environmental standards; IEC 61215 / IEC 61730 Application Class A certifications|
|Front Glass||0.13 inch tempered glass|
|Junction Box Type||IP65 rated MC4|
|Dimensions||64.409 X 38.898 X 1.57 Inches|
|Certification Approvals / Listed||UL/US, SA/US, BRE Global Listed, TUV Rheinland ID:0000024963, PV Cycle Association, CE, ISO 9001, ISO 14001, GB/T 28001|
|Solar Panel Warranty||Output warranty of 80% performance Pmpp (STC) 25 years|
Enphase Energy 11000W Documents & Manuals
Enphase Energy 11000W Gridtie System Do-It-Yourself Home Solar System
Enphase Energy 11000W Solar Package; The Enphase system maximizes energy production from your array using some very simple principles. Each Enphase microinverter is individually connected to one solar panel in your array. This unique configuration means that an individual Maximum Peak Power Point Tracker (MPPT) controls each solar panel. This ensures that the maximum power available from each solar panel is exported to the utility grid regardless of the performance of the other solar panel in the array. That is, although individual 245 watt solar panels in the array may be affected by shading, soiling, orientation, or solar panel mismatch, the Enphase microinverter ensures top performance for each panel. The result is maximum energy production from your solar array.
Our 11000W kit is relatively simple to layout and install. You will not need string calculations, just keep your string to a maximum of 17 245 watt panels, and you can install individual solar panels in any combination of solar panel quantity, type, age and orientation. Each microinverter quickly mounts on the roof or ground rack (optional), directly beneath each solar panel. Low voltage DC wires connect from the solar panel via waterproof MC4 connectors directly to the co-located microinverter.
Simple Overview of the Installation Procedure:
- Step 1 – Measure AC at the Electrical Utility Connection (See Enphase installation instruction sheet under "Documents" tab above)
- Step 2 – Install the AC Branch Circuit Junction Box (Not included)
- Step 3 – Position the Enphase Engage Cable
- Step 4 – Attach the microinverter to the Solar Racking (Optional)
- Step 5 – Dress the Enphase Engage Cable
- Step 6 – Terminate the Unused End of the Engage Cable
- Step 7 – Connect the Engage Cable to AC Junction Box
- Step 8 – Ground the System
- Step 9 – Complete the Installation Map
- Step 10 – Connect the 245 Watt Solar Panels
- Step 11 – Build the Virtual Array
Blue Pacific Solar has provided all of the main parts you will need for your 11000W solar kit. Here are some additional items that your may need prior to installing your package. Conduit, appropriately sized electrical wire, some fasteners and grounding rod and wire. Building and installing your own home solar system is not only the smart choice for controlling your expenses, it may be on the most satisfying DIY projects you ever have undertaken.
NOTE, IMPORTANT Enphase Energy 11000W Package INSTALLATION: (OK, here is the scary legal disclaimer.) It is the responsibility of the purchaser to ensure that all products are installed and operated in accordance with local and national building codes as specific by the NEC (National Electric Code), UBC (Uniform Building Code) or IBC (International Building Code) and local utility company policy. These codes may vary from city to city and county to county. All Grid-tied solar installations should be permitted and inspected, where required, by the local inspection authority in the same manner as other equivalent electrical systems. One last thing. It is always a good idea to contract with a local licensed electrician to at least do the final electrical connection of your PV system from the AC disconnect to your home utility breaker box. Some local permitting authorities require that a licensed electrician do all the wiring from the rack to the utility interconnect. If you need help with the permitting documents for your 11000W solar kit, we are here for you. Solar permit service add on is available at checkout.
Additional Safety Instructions, 11000W Watt Solar microinverter Kit; Perform all electrical installations in accordance with all applicable local electrical codes and the National Electrical Code (NEC), ANSI/NFPA 70. Be aware that only qualified personnel should install or replace Enphase microinverter. Do not attempt to repair the Enphase microinverter in your 11000W Watt Solar Kit; it contains no user-serviceable parts. If it fails, please contact Enphase customer service to obtain an RMA (return merchandise authorization) number and start the replacement process. Tampering with or opening the Enphase microinverter will void the warranty. Before installing or using the Enphase microinverter, please read all instructions and cautionary markings in the technical description and on the Enphase microinverter System and the solar equipment. Connect the Enphase microinverter to the utility grid only after receiving prior approval from the electrical utility company. Be aware that the body of the Enphase microinverter is the heat sink. Under normal operating conditions, the temperature is 15°C above ambient, but under extreme conditions the microinverter can reach a temperature of 80°C. To reduce risk of burns, use caution when working with microinverter. Do NOT disconnect the solar module from the Enphase microinverter without first removing AC power.
This Enphase Energy 11000W microinverter package is an affordable high quality solution for your home or businesses energy independence. Reducing on-site labor requirements, the system can be expanded at anytime.